Move the air conditioning machines
Air conditioners remove fluoride and heavy machine
1, receivables. Power cooling, compressor close the high pressure valve operation after a minute, close the low pressure valve, shut down. Pull the plug (remember!!!! )
2, open outdoor unit copper pipe fittings (plastic wrap, prevents soil), disconnect the outdoor electrical wire connector (remember the order line)
3, remove indoor and outdoor unit.
1, and according to indoor machine of location played tube of had wall eye son, in scheduled location nail good indoor machine of hanging disc (must guarantee level, with level instrument correction), will tube wear out Hou hanging good indoor machine;
2, and according to tube of length determine outdoor machine of location, outdoor machine also to guarantee level;
3, and received good level pressure tube, first open high pressure valve, then pine low voltage Guan Suomu (discharge pipeline in the of air), heard has outlet of voice 8-10 seconds Hou twist tight the lock mother, Open the low pressure valve, in order the connected wires.
4, powered on and test machine. Use soapy water to check pipe joints (lock) for leaks. BACK PAGE